Minimax SSP 1230 system uses a proprietary continuous linear tube that reliably detects fire and pneumatically actuates release of 3M™ Novec™ 1230 extinguishing agent. It is more flexible, space efficient and cost effective than alternative mechanical or electronic systems.
Install Directly Inside Electrical Cabinets, CNC Machines, or Fume Cabinets
Flexible sensor tubing is easily installed on cabinet or enclosure walls or roofs, or anywhere a fire could likely start. When in service, the tubing is pressurized with dry nitrogen to 240 psi. The dynamics of pressurization make the tubing more reactive to heat.
Early Fire Detection
If a flame-up occurs, the fire's heat causes the pressurized sensor tube to burst at the hottest spot (approximately 240º F).
The sudden tube depressurization actuates the special pressure differential valve and instantly floods the entire cabinet area with Novec™ 1230 extinguishing agent. The fire is quickly suppressed just moments after it began...minimizing damage and downtime.